The Alagasco guy said that the old meter they just installed was broken. So I have a new meter?
I could not get the boiler to cut on, so I hot wired the flow switch. The boiler worked, but I thought the flow switch was broken.
So I took off the flow switch and checked it out. Of course I messed up and the flow switch was fine. I cleaned it up and it has to be the pump.
Not really sure how this pump works, but maybe the problem is the power supply?
I did get the heater to work today.